Power Factor Correction Application Guide
 Phone  : 586.979.9955 Fax  : 586.979.9484

Resources > Engineering Resources > Power Factor Correction

# Application Guide for Power Factor Correction

POWER FACTOR

UNDERSTANDING POWER FACTOR

Loads are predominantly inductive or resistive in most modern electrical distribution systems. Resistive loads include incandescent lighting and resistance heating. Inductive loads include motors, induction furnaces, transformers and ballast-type lighting. Inductive loads, such as motors, require two types of power:

1. Active power to perform the work
2. Reactive power to create and maintain electro-magnetic fields
For a given device, active power varies with changes in load, while reactive power remains constant. The vector sum of the active power and reactive power results in total power. Total power is the power that must be generated by the utility provider for the user.
• Active power, also referred to as real power, working power, or load power is commonly measured in kW (1000 Watts)
• Reactive power, also referred to as imaginary power, inductive power, or magnetizing power is measured in kVAr (1000 volt-amperes reactive)
• Total Power, also referred to as apparent power is measured in kVA (1000 volt-amperes).

A low power factor requires a larger amount of total power for a given amount of active power, whereas a high power factor requires a lesser amount of total power for the same amount of active power. Utilities provide total power to the user, and by means of continuous metering determine actual values of the components of power shown in Figure 1. These values are provided on the monthly billing statements. If a facility operates at a low power factor, the utility provider may add a penalty. In like manner, a high power factor may result in a rebate or credit.

 Home About Products Services Resources FAQ Engineering Resources Power Factor Correction Improving power Factor Elimination of Penalty Dollars Additional Capacity in Electrical System Reduction of I2R Losses Analysis of Utility Bills Method #1 Capacitor at Load Method #2 Fixed Capacitor Bank Method #3 Automatic Capacitor Bank Method #4 Combination of Methods Harmonic Distortion Definitions Basic Relations Harmonic Mitigation Line Reactors Specifications Technical Bulletins - Capacitalks Troubleshooting Product Resources Case Studies Contact Us

### MYRON ZUCKER INC. products are designed to:

• Improve power factor
• Eliminate utility penalties or surcharges
• Increase available distribution capacity
• Mitigate harmonic distortion
• Protect sensitive equipment
• Decrease downtime
• Reduce line losses and associated cost
• Comply with industry standards

### SERVICES

Terms of Sale

Facility Questionnaire