Power Factor Correction Application Guide | Analysis Of Utility Bills
 Phone  : 586.979.9955 Fax  : 586.979.9484

Resources > Engineering Resources > Power Factor Correction > Analysis of Utility Bills

# Application Guide for Power Factor Correction

HOW TO DETERMINE AMOUNT OF kVAr REQUIRED

ANALYSIS OF UTILITY BILLS

Monthly utility bills should be studied and analyzed.  Since loads vary from month to month, or season to season, it is good practice to consider the last twelve months of bills.  Most utility providers print out the average power factor for the month, and the total active energy consumed during that billing period.  However, with some utility providers, power factor may not be obvious on the monthly bill.  Myron Zucker, Inc. (MZI) experienced staff has the expertise to provide detailed utility bill analysis.  The average active power for the billing period can be calculated by dividing the total active energy consumed by the total number of hours of the billing period.

With values of active power and power factor known, the power triangle diagram can be developed and the reactive power can be determined.  To improve the power factor to 100%, the value of reactive power determined from this analysis is equal to the capacitance of the PFCC in kVAr.  Sizing of PFCC can also be determined by the use of Table 1, which simplifies the calculations.

INSTRUCTIONS FOR USING TABLE 1:

1. Find the billing (original) power factor in the first column.
2. Read across the first row for the desired power factor.
3. Find the multiplier value where the above two values intersect.
4. Determine the PFCC capacitance in kVAr by multiplying the average active power by the multiplier value.

EXAMPLE:

The utility bill shows an average power factor of .72 with an average active power of 627 kW. How much capacitance in kVAr is required to improve the power factor to .95?

STEPS:

1. Locate .72 (original power factor) in column (1).
2. Read across desired power factor to .95 column.
3. Find the multiplier value of .635  where the above two values intersect.
4. Multiply the average active power of 627 by .635 (627 kW x .635 = 398 kVAr).
5. Select a 400 kVAr to improve power factor to 95%.
Once capacitance is determined the next task is to determine the PFCC mounting location.

 Home About Products Services Resources FAQ Engineering Resources Power Factor Correction Improving power Factor Elimination of Penalty Dollars Additional Capacity in Electrical System Reduction of I2R Losses Analysis of Utility Bills Method #1 Capacitor at Load Method #2 Fixed Capacitor Bank Method #3 Automatic Capacitor Bank Method #4 Combination of Methods Harmonic Distortion Definitions Basic Relations Harmonic Mitigation Line Reactors Specifications Technical Bulletins - Capacitalks Troubleshooting Product Resources Case Studies Contact Us

### MYRON ZUCKER INC. products are designed to:

• Improve power factor
• Eliminate utility penalties or surcharges
• Increase available distribution capacity
• Mitigate harmonic distortion
• Protect sensitive equipment
• Decrease downtime
• Reduce line losses and associated cost
• Comply with industry standards

### SERVICES

Terms of Sale

Facility Questionnaire